The CAS BACnet Object Monitor is a software designed to run on a Windows computer for the purpose of testing a connection to a BACnet IP device, or to monitor a BACnet IP device. A user can configure BACnet data points either manually through a configuration screen or by importing a configuration file. The user can then view connection and status details of the configure points on the status screen.
Note: If this application is being used on a trial basis, the notification banner will display the “Trial Version Active” message. The Trial Version limits the user to monitor a maximum of 3 BACnet objects.
Contact us directly for support with CAS BACnet Object Monitor.
Q1: No web page appears once the application has started.
A1: Open a web browser and navigate to the address http://localhost:8080/bin/bacnetobjectmonitor/
Q2: I’ve configured the BACnet IP device and objects, but the values are not refreshing and the background in the status page is red.
A2: Make sure that the BACnet IP device is connected and is on the same subnet as the computer this application is installed on.
Also double check the configuration of the device. Check the IP address, Device ID, and network. Check the port.
Q3: I’ve configured BACnet objects, but the default values never change.
A3: Make sure that those objects actually exist and contain values on the BACnet IP device.
Q4: The BACnet IP device got disconnected, what happens?
A4: If the connection to the BACnet IP device is interrupted, or there was no connection in the first place, the table entries for the objects on the Status Page will have a red background indicating a loss of connection.
Q5: How do I check what version of the CAS BACnet Object Monitor I am using?
A5: Browse to the About Page. The About Page contains all the version information of all the protocols and HTTP drivers installed with this application.
|Purchase BACnet Object Monitor
BACnet for Field Technicians (Free!)Learning about BACnet? Want to update your BACnet knowledge? This free EBook will guide you through basic and advanced BACnet topics.You can purchase a hardcopy of this book from Amazon or you can download the BACnet for Field Technicians for free from our website.
Convert to a different protocol
We can convert a BACnet/Ethernet 802.3 or BACnet/IP or BACnet/ MSTP message to just about any other industrial protocol. We can also integrate fire alarm panels, UPS’s, GenSets and dozens of other equipment types so that can be monitored and controlled using BACnet.
We have a huge list of protocols.
CAS is a member of BACnet International
Metasys® as used in this document is a trademark of Johnson Controls, Inc.
BACnet® is a registered trademark of American Society of Heating, Refrigerating and Air-Conditioning Engineers (ASHRAE).